Fire Safety, Maintenance
The FireAngel battery powered alarms have been designed to be installed quickly and simply, without the services of an electrician. The below will give you an overview of installation but please note that each alarm comes with its own installation manual, so please refer to this before installation.
Which room can I install this smoke alarm?
This smoke alarm can be fitted in living rooms, bedrooms, hallways, landings and dining rooms. If you’re looking for an alarm to detect fire in your kitchen, utility room, attic or garage then check out our range of Heat Alarms.
How many alarms do I need to install?
The law and recommendation for how many smoke alarms are required are specific to the area you live in and your property type.
For the fastest detection of fire we recommend you install a smoke alarm in the circulation space on each level of the home (hallway and landing) as well as in living spaces and bedrooms. We would install these alongside heat alarms in the kitchen, garage and attic and have the alarms interlinked so that if one alarm sounds, they all sound.
Where should I position the smoke alarm?
If you’re installing the alarm on a ceiling, then it should be at least 300mm from light fitting and walls – if possible in the centre of the room.
If you’re installing the alarm on a wall then you will need to ensure the alarm is 300mm from the nearest wall, and between 150mm and 300mm below the ceiling.
Smoke alarms should be positioned at no more than 600mm vertically below the highest point in the room.
Installing your alarm.
The battery will now activate. The red indicator LED on the front of the alarm should flash approximately once every 45 seconds to show that the alarm is active.
WARNING: Removing the smoke alarm from its base plate will deactivate the unit and prevent it from detecting smoke.
After fitting the alarm to the base plate, wait for 5 seconds for the alarm to settle, then test the alarm. See alarm testing.