Guidance for where to install your smoke, heat and CO alarms can be found below:
Where your alarm is installed can trigger nuisance alarms if not correctly placed, for example too close to doors or windows.
For more guidance as to where to install your smoke, heat or CO alarm please refer to your alarm’s manual or contact our friendly Customer Support team.
In order to identify how many alarms to install you need to research the guidelines for fire detection that apply in your local area, using regulations such as Building Regulations or the guidance in BS5839-6, and consider your property type; whether that be private owned, rented, new build, renovated etc. The advice below is purely provided for ‘best practice’ and should not be used independently.
If you live in Scotland find out more about the law in your area on our blog post here. (link to homeowner Scottish regulations blog)
Smoke Alarms: To offer high protection FireAngel advise a smoke alarm within the circulation area of each floor of the property, as well as within the main habitable areas such as bedrooms and living room. It’s important to remember that the sensors in all smoke alarms deteriorate after time, at FireAngel we recommend that smoke alarms are replaced every 10 years.
Heat Alarms (Kitchen Alarms): Heat alarms are the only alarm suitable for use within the kitchen as they’re not affected by cooking fumes like traditional smoke alarms. Over 60 Percent of fires start in the kitchen, with cooking and faulty white goods (fridges and tumble driers) being the main causes. FireAngel recommend a heat alarm is fitted in the kitchen, but you can also fit additional heat alarms in the garage and loft to protect these areas.
Carbon Monoxide (CO) alarms: A Carbon Monoxide detector is the only way to be alerted to a carbon monoxide leak; it can’t be smelt, tasted or seen so it’s impossible for human senses to detect. Known as the ‘Silent Killer’, carbon monoxide (CO) occurs when fuels burn incompletely, with common sources being boilers, gas fires and hobs and solid fuel burners. However, carbon monoxide can also pass through walls, so you would also be at risk if a neighbouring property had a leak. FireAngel recommend a CO alarm is installed between 1 m and 3 m away from each fuel-burning appliance, as well as installing additional units in areas such as living rooms and bedrooms where you spend most time whilst at home.
Yes – we have a range of long-life smoke alarms in our range – found here. If you’re looking for a smart smoke alarm with optional notifications and testing via your phone then view our FireAngel Pro Connected alarms.