Specification 10 Year Kitchen Heat Alarm
Mains Powered with 10 Year Lithium Battery Back-up
Designed with installers in mind, this compliant, flexible, easy to fit range delivers advanced sensing technology including Smart RF interlink ensuring your domestic installations are safe for years to come.
Grade D1 as recommended by BS 5839-6
5 Year Warranty
For peace of mind
Our datasheet and manual contain guidance on the product and the latest standards - if you have any additional questions, our team of experts can offer all the support you need, so get in touch!GET IN TOUCH
Wireless interlink made simple with Smart RF technology. Our Specification range allows installers to create a network of mains and/or battery powered alarms in seconds!
Meets BS 5839-6 standards
Patented sensor technology
Designed and developed for kitchens our alarms feature unique Thermistek sensing technology combined with a patented radiant heat dish, high performance thermistor and predictive monitoring to ensure a quicker response.
For wireless interlink
Smart RF Technology
When one alarm sounds, they all sound. Our Specification range features intelligent Smart RF technology - easily create a wireless or hybrid network of Smart RF mains and battery devices to protect the entire property.
Adaptability & flexibility
Remain compliant to meet latest standards whilst delivering the ultimate level of protection that can be instantly enhanced as legislative requirements evolve, and cost-effectively adapted as the safety and welfare needs of tenants change.
FireAngel are committed to developing technologies that ensure the highest level of fire and CO detection to protect all communities.
Our intelligent technology enables wireless communication with other FireAngel devices to provide maximum protection for tenants and properties.
Our products can be easily upgraded at any time in the future, to meet a changes in tenant needs or comply with new legislative requirements.
COMPLETE THE RANGE…
The future of fire safety
FireAngel Specification is leading the way in advanced fire and CO safety.
Designed for use in a kitchen, garage or loft. Our heat alarms provide quick detection of rapid temperature increases. Its reaction to heat rather than smoke makes it ideal for installation in kitchen areas and garages in order to avoid false alarms caused by cooking and vehicle fumes.
A Grade D1 system is required for:
– New or materially altered dwellings, up to three storeys with no floor exceeding 200 m2.
– Existing dwellings with poor or inadequate fire protection, up to three storeys with no floor exceeding 200 m2.
– Individual dwelling units of two or more rooms in Houses in Multiple Occupation (HMOs) of one or two-storeys, with no floor exceeding 200 m2.
There are three Levels of Detection (LD). Generally the greater the fire risk the more comprehensive the system should be.
LD1 = Maximum Protection. Alarms in all circulation spaces that form part of escape routes and all areas where a fire might start.
LD2 = Medium Protection. All circulation spaces and escape routes (e.g.hallways and landings) are covered together with a provision of higher fire risk areas (e.g.kitchen and living rooms).
LD3 = Minimum Protection. Alarms in all circulation spaces that form part of escape routes.
* Ensure that a Grade D1 system is adequate for the dwelling you are installing the alarms in. You can obtain further information from your local fire service or building control department at your local council offices.
Our advanced Smart RF technology allows smoke, heat and CO devices to be interlinked wirelessly. When alarms are interlinked they are able to communicate and will alert at the same time if one of the alarms detects danger – when one sounds, they all sound. In the case of wireless interlink, this communication is in the form of Smart RF technology, which means there’s no need to run cables between the alarms. The FireAngel Specification range of alarms allows a network to be easily extended to include devices across an entire property. For example, a network of 6 x smoke alarms, 2 x heat alarms, 4 x carbon monoxide alarms and a Spec Connected Wireless Gateway will be completely secure and protect a whole property.
If you choose not to add a Gateway upon initial installation, you can add a Gateway to an existing network at any time in the future – this will allow for remote monitoring of devices as the Gateway will communicate with the FireAngel App using an internet connection, however, if the internet connection fails or cuts out the alarms will still continue to work and protect property, no internet connection means you will no receive any push notifications whilst the internet is not working.
Whilst BS 5839-6 has previously been split into six varying Grades, each outlining the level of protection appropriate for certain properties and their corresponding levels of risk, the new update has altered the six sections, removing Grade B and Grade E, whilst Grade D and Grade F have been split into Grade D1 / Grade D2 and Grade F1 / Grade F2 respectively. Grade C has been revised and its recommendations expanded.
The 2019 grading system is as follows:
|Separate detectors, sounders and central control and indicating equipment with back-up power supply that conforms to British Standards BS EN 54.|
|Separate detectors and sounders that are mains powered with back-up power supply and central control equipment.|
|A system of one or more mains powered detectors, each with a tamper‑proof standby supply consisting of a battery or batteries (such as FireAngel’s SM-SN-1 and HM-SN-1 alarm).|
|A system of one or more mains-powered detectors, each with an integral standby supply consisting of a user‑replaceable battery or batteries. (such as FireAngel’s SW1-PF-T and HW1-PF-T alarm).|
|A system of one or more battery-powered detectors powered by a tamper‑proof primary battery or batteries (such as FireAngel’s ST-622, ST-750 alarm).|
|A system of one or more battery-powered detectors powered by a user‑replaceable primary battery or batteries. (such as FireAngel’s SB1-T alarm).|
|Please note: Grades B and E are no longer defined in BS 5839-6:2019.|